Transient Response of Phasor Measurement Units
As has been mentioned before, phasor is a steady-state concept. In its classical interpretation it is a complex number representation of a pure sinusoidal waveform of single frequency although the frequency is not explicitly displayed in the phasor representation. In power systems, usually the implied frequency is the nominal frequency of the power system. However, it is well known that the power system is rarely operating precisely at the nominal system frequency. We have considered the effect of steady-state off-nominal frequency signals on the phasor measurement process in Chapter 3. It is also well-known that the power system voltages and currents have various harmonic, nonharmonic, and transient components. The harmonic and nonharmonic (steady-state) components are filtered to various degrees by appropriate analog or digital filters.
There are transient phenomena occurring on power systems due to a variety of causes which produce transient components in current and...
KeywordsPower System Phasor Estimate Data Window Voltage Transformer Phasor Measurement Unit
- 1.Greenwood, A., “Electrical transients in power systems” (book) Wiley Inter-science, 1971.Google Scholar
- 2.Chowdhuri, P., “Electromagnetic transients in power systems” (book) Research Studies Press Ltd., John Wiley 8 Sons, Inc., 1996.Google Scholar
- 3.Phadke, A.G., Kasztenny, B., “Synchronized phasor and frequency measurement under transient conditions”, Accepted for publication in IEEE Transac-tions on Power Delivery, 2008.Google Scholar
- 4.Horowitz, S.H. and Phadke, A.G., “Power system relaying”, (book), John Wiley & Sons, Second Edition, 4th printing,Google Scholar
- 5.Seljeseth, H. et al., “Voltage transformer frequency response. Measuring harmonics in Norwegian 300 kV and 132 kV Power Systems”, 8th International Conference on Harmonics and Quality of Power, ICHQP '98, IEEE/PES and NTUA, Athens, Greece, October 14–16, 1998.Google Scholar
- 6.Meliopoulos, A.P.S. et al., “Transmission level instrument transformers and transient event recorders characterization for harmonic measurements”, IEEE Transactions on Power Delivery, Vol. 8, No. 3, July 1993.Google Scholar
- 7.Working Group C-5 of IEEE Power System Relaying Committee, “Mathemati-cal models for current, voltage, and coupling capacitor voltage transformers”, IEEE Transactions on Power Delivery, Vol. 15, No. 1, January 2000.Google Scholar
- 9.Phadke, A.G. and Thorp, J.S., “Computer relaying for power systems, (book), Research Studies Press, Reprinted May, 2000, p 150.Google Scholar