Skylight Optimization Design Based on the Interior Ventilation in the Office Building in Cold Region
The severe climate in cold regions imposes strict requirements with respect to building energy savings and challenges indoor environmental comfort levels. The atrium has an important influence on indoor ventilation performance, which is a function of both wind pressure action and thermal pressure action. Specifically, skylights are a significant element for atrium ventilation and their ability to affect atrium ventilation performance and their optimization design strategies need to be studied. This chapter uses Ansys-Airpak ventilation simulation software to explore the skylight’s influence on natural ventilation with its three variables: plane position, distribution pattern, and skylight height. Through the simulation, the research leads to three conclusions: (1) skylight outlets should be set on the side behind the wind direction, which is useful for air flow because of the wind pressure; (2) outlets should be set around the skylight uniformly to accelerate the air exchange rate; and (3) the skylight height design should be combined with atrium size and outlet location. Overall, skylights have a significant influence on atrium ventilation performance and should be designed carefully to reduce energy consumption and increase the indoor environmental comfort level.
KeywordsAtrium Natural ventilation Skylight design Cold region
This work was sponsored by the Heilongjiang Natural Science Foundation (E201317).
- 1.yuan MH (2012) Cold region architecture. China Architecture & Building Press, Beijing, pp 3–6Google Scholar
- 2.Kotani H, Sagara K, Yamanaka T et al (2006) Task ambient air conditioning system with natural ventilation for high rise office building (Part 2: measurement of natural ventilation rate and CFD analysis using measured data). Balance 9:3.2–2.7Google Scholar
- 3.Du Tiantian (2014) Simulation and optimization design study of the cold place office building’s atrium skylight. Harbin Institute of Technology, 51–76.Google Scholar
- 4.Zhou L, Huang H, Shakeri A et al (2005) Indoor environment in an office floor with nozzle diffusers: a CFD simulation. Proceedings of building simulation conference, 67–69Google Scholar
- 5.Hayashi T, Ito K (2012) Coupled simulation of BES-CFD and performance assessment of energy recovery ventilation system for office model. J Cent South Univ 3:008Google Scholar
Open Access This chapter is licensed under the terms of the Creative Commons Attribution-NonCommercial 2.5 International License (http://creativecommons.org/licenses/by-nc/2.5/), which permits any noncommercial use, sharing, adaptation, distribution and reproduction in any medium or format, as long as you give appropriate credit to the original author(s) and the source, provide a link to the Creative Commons license and indicate if changes were made.
The images or other third party material in this chapter are included in the chapter's Creative Commons license, unless indicated otherwise in a credit line to the material. If material is not included in the chapter's Creative Commons license and your intended use is not permitted by statutory regulation or exceeds the permitted use, you will need to obtain permission directly from the copyright holder.