Water chemistry of the secondary circuit at a nuclear power station with a VVER power reactor
- 35 Downloads
Results of implementation of the secondary circuit organic amine water chemistry at Russian nuclear power plant (NPP) with VVER-1000 reactors are presented. The requirements for improving the reliability, safety, and efficiency of NPPs and for prolonging the service life of main equipment items necessitate the implementation of new technologies, such as new water chemistries. Data are analyzed on the chemical control of power unit coolant for quality after the changeover to operation with the feed of higher amines, such as morpholine and ethanolamine. Power units having equipment containing copper alloy components were converted from the all-volatile water chemistry to the ethanolamine or morpholine water chemistry with no increase in pH of the steam generator feedwater. This enables the iron content in the steam generator feedwater to be decreased from 6–12 to 2.0–2.5 μg/dm3. It is demonstrated that pH of high-temperature water is among the basic factors controlling erosion and corrosion wear of the piping and the ingress of corrosion products into NPP steam generators. For NPP power units having equipment whose construction material does not include copper alloys, the water chemistries with elevated pH of the secondary coolant are adopted. Stable dosing of correction chemicals at these power units maintains рН25 of 9.5 to 9.7 in the steam generator feedwater with a maximum iron content of 2 μg/dm3 in the steam generator feedwater.
Keywordswater chemistry erosion-and-corrosion wear high-temperature pH morpholine ethanolamine
Unable to display preview. Download preview PDF.
- 1.V. A. Mamet and O. I. Martynova, “Hide out (local concentration) processes of boiler water impurities in NPP steam generators and their influence on equipment operation reliability,” Teploenergetika, No. 7, 2–7 (1993).Google Scholar
- 2.E. A. M. Wetton and G. G. Lewis, “High temperature pH calculation for solutions of volatile amines,” in Proc. 4th BNES Conf. on Water Chemistry of Nuclear Reactor Systems, London, Oct. 13–17, 1986 (Thomas Thelford, London, 1986).Google Scholar
- 3.Pressurized Water Reactor Secondary Water Chemistry Guidelines. Revision 6 (Electric Power Res. Inst., Palo Alto, CA, 2004).Google Scholar
- 4.PWR Advanced All-Volatile Treatment Additives, By-Products and Boric Acid: EPRI Project S409-2 Final Report (San Diego Univ., San Diego, CA, 1992).Google Scholar
- 5.R. M. Donaldson, M. F. Fountain, J. C. Green G. G. Lewis, J. D. Tyldesley, and E. A. M. Wetton, “Selection of amines for use as alkalising agents in the steam-water circuits of nuclear power plant,” in Proc. BNES Conf. on Water Chemistry of Nuclear Reactor Systems, Bournemouth, Oct. 12–15, 1992 (Br. Nucl. Energy Soc., London, 1992).Google Scholar
- 6.Richtlinie für das Wasser in Kernkraftwerken mit Leichtwasserreaktoren, 3rd ed. (VGB PowerTech, 2006).Google Scholar
- 7.STO 1.1.1.07.003.0818-2016. Water Chemistries of the Secondary Circuit of a Nuclear Power Plant with VVER-1000. Quality Standards for the Working Medium and the Means for Their Support (Rosenergoatom, Moscow, 2016).Google Scholar