Localized airflow can result in both temperature and pollutant concentration segregations with limited mixing between adjacent environmental zones. However, when the bacteria source is within the environmental zone, it becomes important to look for effective methods to disinfect the localized air and prevent cross-infection among occupants in the same zone. This work investigates the effectiveness of upper-room ultraviolet germicidal irradiation (UVGI) in reducing airborne bacteria transmission within a zone conditioned by localized ceiling-mounted airconditioning system that recirculates return air. A computational fluid dynamics (CFD) model was developed to simulate the transport and inactivation by UV of Serratia marcescens, an extremely UV-susceptible microorganism. The CFD–UV model was validated using measurements of airflow, temperature, and UV irradiance. Numerous CFD simulations were performed for a case study to determine the maximal fraction of return air that can be recirculated for energy conservation without violating the indoor air quality standards for CO2 and bacteria concentrations. Results revealed that a maximum of 23% return air can be tolerated when minimal UV output of 15 W is delivered to the space. The use of the optimal setting reduced the energy consumption of the system by 15% compared to 100% fresh air case without UVGI.
This is a preview of subscription content, access via your institution.
Buy single article
Instant access to the full article PDF.
Tax calculation will be finalised during checkout.
American Conference of Governmental Industrial Hygienists (2012). 2012 TLVs and BEIs. Cincinnati: ACGIH Signature Publications.
ANSYS (2012). ANSYS Fluent 14.5.
Ariff M, Salim MS, Cheah SC (2009). Wall y+ approach for dealing with turbulent flow over surface mounted cube: Part2—High Reynolds number. In: Proceedings of 7th International Conference on CFD in the Minerals and Process Industries CSIRO, Melbourne, Australia.
ASHRAE (2004). ANSI/ASHRAE Standard 55-2004, Thermal Environmental Conditions for Human Occupancy. Atlanta: American Society of Heating, Refrigeration and Air-Conditioning Engineers.
ASHRAE (2007a). ANSI/ASHRAE Standard 62.1-2007, Ventilation for Acceptable Indoor Air Quality. Atlanta: American Society of Heating, Refrigerating and Air-conditioning Engineers.
ASHRAE (2007b). ASHRAE Standard 52.2-2007, Method of Testing General Ventilation Air-cleaning Devices for Removal Efficiency by Particle Size. Atlanta: American Society of Heating, Refrigerating and Air-conditioning Engineers.
Beggs CB, Kerr JG, Donnelly JK, Sleigh PA, Mara DD, Cairns G (2000). The resurgence of tuberculosis in the tropics. An engineering approach to the control of Mycobacterium tuberculosis and other airborne pathogens: A UK hospital based pilot study. Transactions of the Royal Society of Tropical Medicine and Hygiene, 94: 141–146.
Chen Q, Srebric J (2000). Simplified diffuser boundary conditions for numerical room airflow models. Final Report for ASHRAE RP- 1009, Massachusetts Institute of Technology, USA.
Chmielewski M, Gieras M (2013). Three-zonal wall function for k–e turbulence models. Computational Methods in Science and Technology (CMST), 19: 107–114.
Fennelly KP, Martyny JW, Fulton KE, Orme IM, Cave DM, Heifets LB (2004). Cough-generated aerosols of Mycobacterium tuberculosis. A new method to study infectiousness. American Journal of Respiratory and Critical Care Medicine, 169: 604–609.
First M, Rudnick SN, Banahan KF, Vincent RL, Brickner PW (2007). Fundamental factors affecting upper-room ultraviolet germicidal irradiation—Part I. Experimental. Journal of Occupational and Environmental Hygiene, 4: 321–331.
Gao NP, Niu JL (2007). Modeling particle dispersion and deposition in indoor environments. Atmospheric Environment, 41: 3862–3876.
Gupta JK, Lin CH, Chen Q (2010). Characterizing exhaled airflow from breathing and talking. Indoor Air, 20: 31–39.
Gilkeson CA, Noakes C (2013). Application of CFD simulation to predicting upper-room UVGI effectiveness. Photochemistry and Photobiology, 89: 799–810.
Hathway EA, Noakes CJ, Sleigh PA, Fletcher LA (2011). CFD simulation of airborne pathogen transport due to human activities. Building and Environment, 46: 2500–2511.
Joubert A, Laborde JC, Bouilloux L, Chazelet S, Thomas D (2011). Modelling the pressure drop across HEPA filters during cake filtration in the presence of humidity. Chemical Engineering Journal, 166: 616–623.
Kanaan M, Ghaddar N, Ghali K, Araj G (2014). New airborne pathogen transport model for upper-room UVGI spaces conditioned by chilled ceiling and mixed displacement ventilation: Enhancing air quality and energy performance. Energy Conversion and Management, 85: 50–61.
Ko G, First MW, Burge HA (2000). Influence of relative humidity on particle size and UV sensitivity of Serratia marcescens and Mycobacterium bovis BCG aerosol. Tubercle and Lung Disease, 80: 217–228.
Kujundzic E, Hernandez M, Miller SL (2007). Ultraviolet germicidal irradiation inactivation of airborne fungal spores and bacteria in upper-room air and HVAC in-duct configurations. Journal of Environmental Engineering and Science, 6: 1–9.
Lai ACK, Nazaroff WW (2000). Modeling indoor particle deposition from turbulent flow onto smooth surfaces. Journal of Aerosol Science, 31: 463–476.
Lai KM, Burge HA, First MW (2004). Size and ultraviolet germicidal irradiation susceptibility of Serratia marcescens when aerosolized from different suspending media. Applied and Environmental Microbiology, 70: 2021–2027.
Li Y, Zhao B (2012). Application of building simulation tools for studying airborne infection and its control. Building Simulation, 5: 3–4.
Lindsley WG, King WP, Thewlis RE, Reynolds JS, Panday K, Cao G, Szalajda JV (2012). Dispersion and exposure to a cough-generated aerosol in a simulated medical examination room. Journal of Occupational and Environmental Hygiene, 9: 681–690.
Lo LJ, Novoselac A (2010). Localized air-conditioning with occupancy control in an open office. Energy and Buildings, 42: 1120–1128.
Makhoul A, Ghali K, Ghaddar N, Chakroun W (2013). Investigation of particle transport in offices equipped with ceiling-mounted personalized ventilators. Building and Environment, 63: 97–107.
Memarzadeh F, Xu W (2012). Role of air changes per hour (ACH) in possible transmission of airborne infections. Building Simulation, 5: 15–28.
Miller FJ, Gardner DE, Graham JA, Lee Jr RE, Wilson WE, Bachmann JD (1979). Size considerations for establishing a standard for inhalable particles. Journal of the Air Pollution Control Association, 29: 610–615.
Morawska L (2006). Droplet fate in indoor environments, or can we prevent the spread of infection? Indoor Air, 16: 335–347.
Nicas M, Nazaroff W, Hubbard A (2005). Toward understanding the risk of secondary airborne infection: Emission of respirable pathogens. Journal of Occupational and Environmental Hygiene, 2: 143–154.
Noakes C, Beggs C, Sleigh P (2004). Modelling the performance of upper room ultraviolet germicidal irradiation devices in ventilated rooms: Comparison of analytical and CFD methods. Indoor and Built Environment, 13: 477–488.
Oh MS, Ahn JH, Kim DW, Jang DS, Kim Y (2014). Thermal comfort and energy saving in a vehicle compartment using a localized air-conditioning system. Applied Energy, 133: 14–21.
Papineni RS, Rosenthal FS (1997). The size distribution of droplets in the exhaled breath of healthy human subjects. Journal of Aerosol Medicine: Deposition, Clearance, and Effects in the Lung, 10: 105–116.
Patankar SV (1980). Numerical Heat Transfer and Fluid Flow. Washington DC: Hemisphere.
Rahn RO, Xu P, Miller SL (1999). Dosimetry of room-air germicidal irradiation using spherical actinometry. Photochemistry and Photobiology, 70: 314–318.
Rudnick SN, First MW (2007). Fundamental factors affecting upper-room ultraviolet germicidal irradiation—Part II. Predicting effectiveness. Journal of Occupational and Environmental Hygiene, 4: 352–362.
Schmidt MG, Attaway HH, Terzieva S, Marshall A, Steed LL, Salzberg D, Hamoodi HA, Khan JA, Feigley CE, Michels HT (2012). Characterization and control of the microbial community affiliated with copper or aluminum heat exchangers of HVAC systems. Current Microbiology, 64: 141–149.
Speziale CG (1987). On nonlinear k–l and models of turbulence. Journal of Fluid Mechanics, 178: 459–475.
Srebric J, Chen Q (2001). A method of test to obtain diffuser data for CFD modeling of room airflow. ASHRAE Transactions, 107(2): 108–116.
Singh P, Mahajan RP, Murty GE, Aitkenhead AR (1995). Relationship of peak flow rate and peak velocity time during voluntary coughing. British Journal of Anesthesia, 74: 714–716.
Sung M, Kato S (2010). Method to evaluate UV dose of upper-room UVGI system using the concept of ventilation efficiency. Building and Environment, 45: 1626–1631.
Van Sciver M, Miller S, Hertzberg J (2011). Particle image velocimetry of human cough. Aerosol Science and Technology, 45: 415–422.
Wainwright CE, France MW, O’Rourke P, Anuj S, Kidd TJ, Nissen MD, Sloots TP, Coulter C, Ristovski Z, Hargreaves M, Rose BR, Harbour C, Bell SC, Fennelly KP (2009). Cough-generated aerosols of Pseudomonas aeruginosa and other Gram-negative bacteria from patients with cystic fibrosis. Thorax, 64: 926–931.
Wan M, Chao C (2005). Numerical and experimental study of velocity and temperature characteristics in a ventilated enclosure with under floor ventilation systems. Indoor Air, 15: 342–355.
Wells WF (1934). On air-borne infection. Study II. Droplets and droplet nuclei. American Journal of Hygiene, 20: 611–618.
WHO (1988). Indoor air quality: Biological contaminants. World Health Organization, European Series, n. 31, Copenhagen, Denmark.
Wu CL, Yang Y, Wong SL, Lai ACK (2011). A new mathematical model for irradiance field prediction of upper-room ultraviolet germicidal systems. Journal of Hazardous Materials, 189: 173–185.
Xu PJ, Peccia J, Fabian P, Martyny JW, Fennelly KP, Hernandez M, Miller SL (2003). Efficacy of ultraviolet germicidal irradiation of upper-room air in inactivating airborne bacterial spores and mycobacteria in full-scale studies. Atmospheric Environment, 37: 405–419.
Xu Z, Shen F, Li X, Wu Y, Chen Q, Jie X, Yao M (2012). Molecular and microscopic analysis of bacteria and viruses in exhaled breath collected using a simple impaction and condensing method. PLoS ONE, 7: e41137.
Zhang Z, Chen Q (2007). Comparison of the Eulerian and Lagrangian methods for predicting particle transport in enclosed spaces. Atmospheric Environment, 41: 5236–5248.
About this article
Cite this article
Kanaan, M., Ghaddar, N. & Ghali, K. Localized air-conditioning with upper-room UVGI to reduce airborne bacteria cross-infection. Build. Simul. 9, 63–74 (2016). https://doi.org/10.1007/s12273-015-0250-7
- microorganism transport
- air quality
- localized air-conditioning
- return air ratio
- ultraviolet germicidal irradiation