This paper presents the decay characteristics of expiratory aerosol using large-eddy simulations coupled with Lagrangian particle tracking for evaluating the prevention of pathogen infection in a typical indoor environment. Ten cases of enclosed-rooms with five different diffuser-induced airflow patterns were investigated. For particles about 10 μm in diameter, which closely approximates the mean diameter of expiratory aerosol, the decay characteristics of each case with no obstacles proved that the most efficient case was the floor-supplied displacement type, followed by the ceiling-mounted line diffuser, floor-mounted diffuser, and ceiling-mounted square diffuser. The least effective case was the ceiling-mounted four-way cassette-type air diffuser under the same air changes per hour. However, in the situation of obstacles representing human bodies, the floor- supplied displacement type showed worse decay characteristics because of preventing the “piston flow-like” one-direction flow. On the other hand, the diffuser cases of the ceiling-mounted square type and the ceiling-mounted four-way cassette-type showed improved decay speed by exhaust and deposition. In particular, the ceiling-mounted square diffuser showed the most effective removal performance. These results imply that the flow configurations that induce small circulation caused by the inlet-outlet layout tend to improve the decay characteristics in terms of “the robust flow design” in a situation of complex flow field.
Berrouk AS, Lai ACK, Cheung ACT, Wong SL (2010). Experimental measurements and large eddy simulation of expiratory droplet dispersion in a mechanically ventilated enclosure with thermal effects. Building and Environment, 45: 371–379.
Bolashikov ZD, Melikov AK (2009). Methods for air cleaning and protection of building occupants from airborne pathogens. Building and Environment, 44: 1378–1385.
Chao CYH, Wan MP, Morawska L, Johnson GR, Ristovski ZD, Hargreaves M, Mengersen K, Corbett S, Li Y, Xie X, Katoshevski D (2009). Characterization of expiration air jets and droplet size distributions immediately at the mouth opening. Journal of Aerosol Science, 40: 122–133.
Chao CYH, Wan MP (2006). A study of the dispersion of expiratory aerosols in uni-directional downward and ceiling-return type airflows using multiphase approach. Indoor Air, 16: 296–312.
Kato S, Murakami S (1992). New scales for evaluating ventilation efficiency as affected by supply and exhaust openings based on spatial distribution of contaminant. In: Proceedings of International Symposium on Room Air Convection and Ventilation Effectiveness, Tokyo, Japan, pp.321–332.
Klepeis NE, Nelson WC, Ott WR, Robinson JP, Tsang AM, Switzer P, Behar JV, Hern SC, Engelmann WH (2001). The National Human Activity Pattern Survey (NHAPS): A resource for assessing exposure to environmental pollutants. Journal of Exposure Analysis and Environmental Epidemiology, 11: 231–252.
Smagorinsky J (1963). General circulation experiments with the primitive equations, in the basic experiment. Monthly Weather Review, 91: 99–164.
Sung M, Kato S (2010). Method to evaluate UV dose of upper-room UVGI system using the concept of ventilation efficiency. Building and Environment, 45: 1626–1631.
Wan MP, Chao CYH (2007). Transport characteristics of expiratory droplets and droplet nuclei in indoor environments with different ventilation airflow patterns. Journal of Biomechanical Engineering, 129: 341–353.
Weiss RA, McMichael AJ (2004). Social and environmental risk factors in the emergence of infectious diseases. Nature Medicine, 10: S70–S76.
Weller HG, Tabor G, Jasak H, Fureby C (1998). A tensorial approach to computational continuum mechanics using object-oriented techniques. Computers in Physics, 12: 620–631.
Zhang, Z, Zhang W, Zhai Z, Chen Q (2007). Evaluation of various turbulence models in predicting airflow and turbulence in enclosed environments by CFD: Part 2-Comparison with experimental data from literature. HVAC & Research, 13: 871–886.
About this article
Cite this article
Hasama, T. Decay characteristics of expiratory aerosol in various diffuser-induced airflow patterns using large-eddy simulation. Build. Simul. 6, 225–233 (2013). https://doi.org/10.1007/s12273-013-0108-9
- large-eddy simulation
- expiratory aerosol
- indoor pathogen infection
- air diffuser layout
- airflow pattern
- human body