Problems of vulnerability of low-temperature rotors of cogeneration steam turbines to damage
- 23 Downloads
Statistics of damage of steam turbine disks operating in the zone of phase transformation is analyzed and it is inferred that it is possible and expedient to determine group lives of rotor parts experiencing the action of permanent and objective negative factors. Statistics of damage in the form of circular cracks in low-temperature rotors of steam turbines of various types is presented.
Keywordssteam turbine low-temperature rotor service life of low-temperature rotors circular cracks rotor blades disks stress concentration corrosion-induced damage zone of phase transformation
Unable to display preview. Download preview PDF.
- 1.GOST 24287-89. Stationary Steam Turbine Installations for Driving Electric Generators of Thermal Power Plants [in Russian].Google Scholar
- 2.G. D. Barinberg, “Raising the efficiency of cogeneration turbines at active combined heat power plants,” Teploénergetika, No. 8 (1997).Google Scholar
- 3.M. B. Coyle and S. J. Watson, “Fatigue strength of turbine shafts with shrunk-on disks,” Proc. Inst. Mech. Eng., 178 (Part. I, No. 6) (1963–1964).Google Scholar