Degradation of cellulosic insulation in power transformers: a SEC–MALLS study of artificially aged transformer papers
The molecular weight distributions of artificially aged transformer papers were studied using SEC–MALLS with 0.5 % DMAc/LiCl as solvent, providing chain length distributions and averages. The slow dissolution and presence of non-cellulosic contaminants tend in some cases to introduce errors in the DPw estimates, and a modified data processing procedure was developed to correct for extraneous scattering. Data were compared to the intrinsic viscosities obtained in 0.5 M Cuen and the ‘viscosimetric DP’ calculated thereof according to ISO 5351. DPvisc was 2–3 times lower than the weight average DP (DPw), but closer to or slightly above the number average DP (DPn) obtained by SEC–MALLS in the case of pure cellulose. Ageing of transformer papers were in some cases associated with changes in the polydispersity (DPw/DPn). The apparent degradation rate (defined as δ(1/DP)/δt) gradually decreased with time, resulting in a tendency for a ‘level-off’ DP in the range 200–300 for DPvisc and DPn, and roughly 1,000 for DPw.
KeywordsCellulose Viscometry Size-exclusion chromatography Multi-angle laser light scattering Transformer paper Ageing
K.B. Liland, M.-H. G. Ese and L. Lundgaard (SINTEF Energy AS) are thanked for providing the aged samples. Cecilie M. Selsbak is acknowledged for performing viscometric measurements. We cordially thank Prof. A. Potthast, University of Natural Resources and Applied Life Sciences (BOKU), Vienna, Austria for valuable discussions and advice regarding SEC–MALLS of cellulosics. The work was supported by the Norwegian Research Council (Grant 173142/30), Hafslund Nett, Statnett SF, Statkraft Energi AS, Norsk Hydro, EDF, Nynäs AB, and ABB through the SINTEF Energy project “Thermal and electromagnetic performance of transformers”.
- ASTMD4243-99 (2004) Standard test method for measurement of average viscometric degree of polymerization of new and aged electrical papers and boards. ASTM International. doi: 10.1520/D4243-99R04E01
- Ford JG, Palumbo AJ (1967) Treated cellulosic material and electrical apparatus embodying the same. 11 April, 1967. US Patent 3313879Google Scholar
- ISO5351 (2009) Determination of limiting viscosity number in cupriethylenediamine (CED) solution. ISO (International Organization for Standardization), Geneva, SwitzerlandGoogle Scholar
- Liland KB, Ese MHG, Selsbak CM, Lundgaard L (2011a) Ageing of oil impregnated thermally upgraded papers oxidation and hydrolysis. In: 2011 IEEE international conference on dielectric liquids (ICDL)Google Scholar
- Silva AA, Laver ML (1997) Molecular weight characterization of wood pulp cellulose: dissolution and size exclusion chromatographic analysis. Tappi J 80:173–180Google Scholar
- Sjöholm E, Gustafsson K, Norman E, Colmsjö A (1997) The effect of degradation on the strength of hardwood kraft pulp fibres. In: ISWPC—9th international symposium on wood and pulping chemistry: poster presentations, pp 1061–1064Google Scholar
- Striegel AM, Timpa JD (1996) Size exclusion chromatography of polysaccharides in dimethylacetamide–lithium chloride. In: Potschka M, Dubin PL (eds) Strategies in size exclusion chromatography, vol ACS Symposium Series 635. American Chemical Society, Washington DC, pp 366–378Google Scholar
- Tanford C (1961) Physical chemistry of macromolecules. Wiley, New YorkGoogle Scholar
- Westinghouse (1965) Insuldur insulation. Descriptive Bulletin, vol DB 45-451. Westinghouse Electric Corporation, USAGoogle Scholar