Microstructure and stress corrosion resistance of alloys X750, 718, and A286 in light water reactor environments
- 314 Downloads
The results of microstructural characterization and stress corrosion cracking tests are presented for several heat treatment conditions of the age-hardenable Alloys X750, 718, and A286. Resistance to intergranular stress corrosion cracking (IGSCC) was evaluated using slow strain rate tests in pressurized water reactor (PWR) primary water, microstructural etch, and rising-load screening tests. The results of these tests indicate greater IGSCC resistance in the PWR primary water environment for X750 microstructures with heavier grain boundary coverage by Cr23C6, regardless of grain boundary chromium depletion. Alloys 718 and A 286 were not highly SCC susceptible according to these screening tests, although they are not immune to IGSCC in reactor environments. Results are compared with those of a related program, including crack initiation and crack growth tests in pressurized and boiling water reactor (BWR) environments.
KeywordsSlow Strain Rate Pressurize Water Reactor Slow Strain Rate Test Boiling Water Reactor Domian
Unable to display preview. Download preview PDF.
- 1.Metals Handbook, T. Lyman, et al., eds., 8th ed., Vol. 8, American Society for Metals, Metals Park, Ohio, 1973, p. 39.Google Scholar
- 3.E.L. Raymond:Trans. Met. Soc. AIME, Vol. 239, No. 9, 1967, pp. 1415–1422.Google Scholar
- 4.K. Hosoi, S. Hattori, Y. Urayama, I. Masaoka, and R. Sasaki,Proc. of the Int’I. Symp. on Environmental Degradation of Materials in Nuclear Power Systems— Water Reactors, Nat’l. Assn. of Corrosion Engineers, Houston, 1984, pp. 334–344.Google Scholar
- 5.F.J. Rizzo and J.D. Buzzanell,J. of Metals, October 1969, pp. 24–33.Google Scholar
- 6.L.E. Davis, N.C. MacDonald, P.W. Palmberg, G.E. Riach, and R.E. Weber,Handbook of Auger Electron Spectroscopy, 2nd ed., Physical Electronics Industries, Inc., Eden Prarie, Minn., 1976, p. 13.Google Scholar
- 9.I.L.W. Wilson and T.R. Mager,Corrosion, Vol. 42, No. 6, 1986, pp. 352–361.Google Scholar
- 10.D.L. Baty, G.O. Hayner, G.S. Clevinger, and G.L. Garner,Proc. of Intl. Symp. on Environmental Degradation of Materials in Nuclear Power Systems—Water Reactors, Nat’l. Assn. of Corrosion Engineers, Houston, 1984, pp. 151–178.Google Scholar
- 11.S. Hattori, Y. Mori, I. Masaoka, R. Sasaki, R. Watanabe, and H. Itoh,Proc. of ANS Winter Annual Meeting, San Francisco, Calif., Nov. 29-Dec. 4, 1981, pp. 451–453.Google Scholar
- 12.G.P. Airey, “Optimization of Metallurgical Variables to Improve the Stress Corrosion Resistance of Inconel 600,”Research Report NP-135, Electric Power Research Institute, Palo Alto, Calif., March 1980.Google Scholar
- 13.D. Van Rooyen,Corrosion, Vol. 31, No. 9, 1975, p. 327.Google Scholar
- 14.H.A. Domian, R.H. Emanuelson, L.W. Sarver, and G.J. Theus,Corrosion, Vol. 33, 1977, p. 26.Google Scholar