Reduction of Inrush Current and Voltage Drop by Selecting Optimum Reactors in Induction Generators
Induction generator has many advantages compared to the synchronous generator in terms of robust, cost and easy to maintenance. So the induction generator has been widely applied to small or medium size hydropower station in recent years. The induction generator generates a large inrush current corresponding to the starting current of the induction motor at the moment of grid connection. This inrush current can cause the voltage drop of the grid as well as the consumer load equipment, which may degrade the stability of the electric quality. It is very important to reduce the voltage drop due to the inrush current in order to improve the electric quality and increase the supply of the induction generator. In this study, we propose a solution to reduce the voltage drop and the inrush current by adjusting the parameters of the reactor tap and adjusting the appropriate operating pattern of the water turbine generator. As a result of the analysis, it was confirmed that the voltage drop can be adjusted within the allowable range.
KeywordsHydropower Induction generator Inrush current Reactor starting Voltage drop
This paper was recommended for best paper award by the ICEMS 2018 Conference.
- 1.MOTIE & KEMCO (2016) New & renewable energy white paper, pp 460–479Google Scholar
- 2.Fritz JJ (1984) Small and mini hydropower systems. McGraw-Hill Book Company, New York CityGoogle Scholar
- 3.Henderson DS (1996) Synchronous or induction Generators?—the choice for small scale generation. IEE Conf, Pub, pp 146–149Google Scholar
- 4.Pankaj KS, Nelson JP (1997) Application guidelines for induction generators. In: Proc. international conference on electrical machines and drives, Milwaukee, Wisconsin, May 18–21, 1997, Paper WC1/5.1–WC1/5.3Google Scholar
- 5.Kim JG, Kim Y (2014) A comparison of the operating characteristics of the synchronous generator and induction generator applied to the small hydroelectric power plant. KIEE 63P(2):55–60Google Scholar
- 7.Shin HJ, Cho MY, Chun HI, Kim JS (2017) A study on the tolerance band of voltage drop during motor startup for refineries and chemical plants with isolated power systems. JEET 12(1):489–493Google Scholar
- 8.Simoes MG, Felix AF (2004) Renewable energy systems-design and analysis with induction generators. CRC, Boca RatonGoogle Scholar
- 9.Kim JG (2014) Operating characteristic analysis of induction generator by the reactor starting. KIEE 63P(3):138–142Google Scholar
- 10.Kim JG (2015) A study on the voltage drop of induction generator along the rotor shape. KIEE 64P(2):62–66Google Scholar
- 11.KEPCO standard (2015) Distributed power distribution system linkage technology guidelineGoogle Scholar
- 12.Dommel HW (1986) Electromagnetic transients program. Reference manual (EMTP theory book). Bonneville Power Administration, PortlandGoogle Scholar