Drinking water should be safe for health and free from amounts of pathogenic microorganisms and parasites posing a threat to human health. In recent years, particular attention has been paid to the threat associated with the operation of hot water installations, potentially providing favourable conditions for the development of bacteria of genera Legionella and Escherichia. Such bacteria are commonly found in the natural environment, but should not reach the consumers’ taps. In this experiment, hot water samples were collected from six public buildings, and the detection of pathogenic microorganisms, namely Legionella spp., Legionella pneumophila, and Escherichia coli bacteria, was performed by means of qPCR analysis. The sequences specific for these bacteria were quantified with TaqMan probes in total DNA extracts of the hot tap water samples. Bacteria of the Legionella spp. type were detected at five sampling sites in the range from 4.52 to 15.59 genomes/mL of hot tap water. Legionella pneumophila was detected at four sampling sites in the range from 0.98 to 11.99 genomes/mL. E. coli was recorded at four sites, but in quantities around 0.00 genomes/mL (less than one genome/mL). This preliminary research points to the need to use molecular techniques as an additional source of information in standard water analyses to obtain shorter detection time and more accurate results.
In favourable environmental conditions, microorganisms can adhere to abiotic surfaces, creating a biofilm structure. This phenomenon often occurs in water supply systems . The presence of biofilm allows the reproduction of potentially pathogenic bacteria due to its organised structure and increased resistance to disinfectants [2, 3]. Despite extensive research conducted on the subject of biofilm adhesion , no methodology has been developed that would prevent its development in real water distribution systems. Therefore, it is necessary to monitor potentially pathogenic microorganisms whose presence can have negative results for consumers. The quality of drinking water, mostly in the case of microbial contamination, is regarded as a serious human health issue . The health risk associated with the presence of opportunistic pathogens in tap water systems attracts more and more scientific attention . Drinking water microbiome is extensively studied, but in the majority of papers the research concerns exclusively cold tap water [7,8,9,10,11,12]. WHO guidelines briefly mention the issue of hot tap water quality, indicating that hot tap water systems should be designed to minimise the proliferation of Legionella . To date, several studies considered the bacterial biodiversity and microbial contamination in hot tap water samples [13,14,15,16]. The majority of them focus on the presence of genus Legionella. Gram-negative bacteria of the Legionella genus present in water supply systems can develop in a wide range of temperatures (25–43 °C, with an optimal spectrum of 30–43 °C) and can survive in a range of 55–60 °C. Such conditions eliminate the competition of other bacteria, facilitating the proliferation of Legionella spp. .
Many approaches are available for the detection and enumeration of representatives of Legionella genus. Standard methods are based on culture media. More advanced methods focus on molecular biology tools. The culture-dependent methods for Legionella detection require the isolation of bacteria on selective agar medium containing l-cysteine, such as buffered charcoal yeast extract (BCYE) agar, supplemented with substances preventing the growth of other genera. The plates should be incubated at ~ 37 °C for 14 day and examined every 2 or 3 days . Some part of viable Legionella cells, however, may be hidden in amoebal hosts, giving false-negative results of incubation . Therefore, the cultivation method is time-consuming (providing results after up to 2 weeks) and may result in underestimations. The other approach for enumeration of Legionella spp. (L. spp.) and Legionella pneumophila (L. pneumophila) in tap water samples involves Legiolert™/Quanti-Tray®, providing acceptable accuracy . Immunodetection is another proposed method, offering the advantage of fast detection . One of the most frequently adopted culture-independent methods for Legionella detection and enumeration is PCR/qPCR. Many DNA sequences have been used to detect Legionella in the PCR approach to date . Moreover, commercial kits for bacterial species detection become more and more popular and widely available. The use of these kits may contribute to the standardisation of the performance of experiments, at least in the laboratory, which repeat the test using the same kits. Despite their reliability, PCR methods applied in Legionella detection may have some hindrances, such as the presence of PCR inhibitors in a sample. Therefore, the employment of internal controls in reactions is recommended .
Escherichia coli (E. coli) is one of the best known and earliest described human opportunistic pathogenic bacteria. Plenty of methods have been developed for its detection and enumeration, including culture-dependent and culture-independent approaches, such as PCR-based methods [22,23,24]. Interestingly, the presence of E. coli strains was detected in tap water distribution systems all over the world, including low-income as well as high-income countries [25,26,27,28]. It is worth mentioning that the potential presence of viable but non-culturable E. coli cells in tap water samples leads to underestimations of the actual tap water contamination .
Both L. spp. and E. coli are considered indicator microorganisms of tap water contamination and are included in hot (L. spp.) and cold (E. coli) tap water routine monitoring in Polish law regulations . Interestingly, the regulations of tap water microbial monitoring focus on living microorganisms, and the recommended methods are unable to detect dead cells (as they are mostly culture dependent).
The objective of this study was to detect the presence and enumerate pathogenic microorganisms in hot tap water samples collected from six buildings of the university campus. The buildings were selected based on their age, as the approximate dates of their construction are known, namely it was possible to evaluate the influence of the internal installations’ age on hot tap water quality. In general, three old and three new buildings were subjected to samples collection. Another objective was to present a fast and accurate method for the detection of microorganisms in tap water which would provide results on the day of sampling. The microorganisms of choice were bacteria from genus Legionella (in terms of the entire genus and L. pneumophila species) and Escherichia (E. coli), because they are the best known and characterised examples of pathogenic bacteria dwelling in tap water.
Samples of hot tap water were collected from six buildings located at the campus of the Wroclaw University of Science and Technology (Fig. 1) during the summer of 2018. The taps were disinfected by alcohol cleaning and submerging the tap spouts in 96% ethanol (Sigma-Aldrich) for 30 s, and water was flushed for 5 min. Each time, 5 L of hot tap water was taken from each site into sterile polypropylene bottles. The water samples were filtered through a sterile filtration set (Nalgene) with a membrane filter of mixed cellulose esters with a pore size of 0.2 μm (Whatman). Then, each filter was placed separately in a sterile flask, filled with 0.85% physiological saline, and shaken for 3 h on a shaker (Nocturne) at 160 rpm. After this time, the flasks were placed in a bath and sonicated for 30 s (35 kHz). The suspensions were concentrated by centrifugation (4000 g, 10 min), and the pellets were subjected to DNA extraction.
To isolate the DNA from the cells, the Isolate II Genomic Kit (Bioline) was used following the manufacturer’s instructions with small modifications. The samples were centrifuged for 10 min at 7500 rpm (Eppendorf mini spin), and then the supernatant was removed. 440 µL of lysis buffer and 25 µL proteinase K (10 mg/mL) were added to each sample. The mixture was intensely vortexed and then incubated at a temperature of 50 °C for approximately 20 min for complete cells lysis. Subsequently, 200 µL of binding buffer was added and the sample was transferred to a silica membrane. The mixture was centrifuged for 2 min at 12,000 rpm. For the neutralisation of the impurities present in the sample, 700 µL Wash buffer reagent dissolved in 96% ethanol (Sigma) was added. The samples were centrifuged for 1 min at 12,000 rpm. The procedure was repeated twice. To release bacterial DNA from the column, 50 µL elution buffer was added directly to a membrane, then incubated for 15 min at room temperature (22 °C) and centrifuged for 1 min at 8000 rpm. Because small amounts of bacterial DNA were expected (due to the medium of interest, i.e. clean tap water after disinfection), the elution buffer volume was reduced in order to obtain a higher DNA concentration. The concentration and purity of the isolated DNA were measured on NanoPhotometer N60 (Implen).
The presence of Legionella spp., L. pneumophila and E. coli was detected by means of AmpliTest (Amplicon). Each set contained primers replicating a genome fragment of bacteria from genera Legionella and Escherichia, specific TaqMan probes, and internal control. With the progress of the process and the hydrolysis of the probe, a fluorescent dye FAM was released, recorded by a real-time PCR apparatus, MIC (Bio Molecular Systems). The detection of internal control was possible due to the release of the HEX fluorescent dye. A negative control (NC) with no DNA and a positive control (PC) containing the DNA of the Legionella spp., L. pneumophila, and E. coli, respectively, were prepared for each set.
All samples were prepared according to the manufacturer’s instructions with a final volume of 20 µL, including 8 µL of DNA sample. The qPCR profile is presented in Table 1. Fluorescence measurement was set on FAM (green) and HEX (yellow) channels after completing the amplification step in each cycle. The same reaction profile was performed for every assay applied in this study.
The quantitative measurement was made by creating a standard curve. Tenfold serial dilutions of genomic DNA extracted from pure strains were prepared for each set. The strains used in the experiment were Legionella pneumophila NCTC 11192/ATCC® 33152 (BioMaxima) for the standard curves in Legionella spp. and Legionella pneumophila assays, and Escherichia coli NCTC 12241/ATCC® 2592 (BioMaxima) for the standard curve in E. coli assay.
The strains were provided in the form of lyophilised discs. Each disc was dissolved in 10 ml of the appropriate sterile broth and incubated at 37 °C for 24 h. After that time, DNA was extracted according to the procedure presented in point 2.2. The DNA concentration was measured in triplicate on a NanoPhotometer N60 (Implen), and the mean value of measurements was considered in further steps. The number of genome copies was calculated based on data obtained from GenBank for appropriate strains and calculated in a DNA calculator (https://cels.uri.edu/gsc/cndna.html). For Legionella spp. and Legionella pneumophila curves, genome length of 3.45892 Mb was assumed (NCBI accession number NC_002942.5), and for E. coli a genome length of 5.130767 Mb was assumed (NCBI accession number NZ_CP009072.1). The calculated values of copies/µL were posted into a qPCR cycler as theoretical amounts. For each standard curve, eight measurement points were prepared, covering the range between 1,780,000 and 0.178 copies/µL in the Legionella spp. and Legionella pneumophila assays, and 1,590,000 and 0.159 copies/µL in the E. coli assay.
Internal control results
To assess the reliability of obtained results, the internal control reaction measurement was performed on the HEX channel. The results suggest the presence of putative inhibitors in the DNA sample from the H-4 building (Table 2).
Detection and quantification of L. spp. sequences
The efficiency of the assay was 0.8896. The dynamic range of the assay covered given concentrations between 1,780,000 and 178 copies/µL. However, all obtained samples’ results were in this range. The standard curve equation was y = −3.618 × + 46.36, where y is Cq and x is log10 of copies/µL (Table 3; Fig. 2).
Detection and quantification of L. pneumophila sequences
The efficiency of the assay was 1.0913. The dynamic range of the assay covered given concentrations between 1,780,000 and 1780 copies/µL. However, all obtained samples’ results were in this range. The standard curve equation was y = −3.121x + 46.27, where y is Cq and x is log10 of copies/µL (Table 4; Fig. 3).
Detection and quantification of E. coli sequences
The efficiency of the assay was 0.9665. The dynamic range of the assay covered given concentrations between 1,590,000 and 1.59 copies/µL. However, all obtained samples’ results were in this range. The standard curve equation was y = −3.121x + 46.27, where y is Cq and x is log10 of copies/µL (Table 5; Fig. 4).
The intense development of civilisation carries with it the risk of creating new environmental pollutants of various levels. Their removal may cause some difficulties. New and quick methods are being sought for the detection and identification of pollutants in the aquatic environment, as well as in the air and in the soil [31,32,33]. Moreover, it is known that the elderly, children, or people with immunocompromise are particularly vulnerable to the presence of pathogenic microorganisms in tap water. It is therefore necessary to use a method with high sensitivity and accuracy. A good example of a fast method suitable for the detection and enumeration of microbial contaminants in water can be the qPCR, as indicated in this study.
The obtained results prove the presence of L. spp., L. pneumophila, and E. coli in hot tap water installations in the majority of examined buildings at the campus of the Wroclaw University of Science and Technology.
Despite the accuracy of the qPCR approach, it is worth emphasising that the method used in this study is not free from limitations, as the environmental samples may contain some qPCR inhibitors. As shown in Table 2, no inhibition was observed, except the DNA sample obtained from hot tap water from building H-4. The presence of inhibitors in DNA sample H-4 is not surprising, because the DNA measurements revealed impurities in the sample (data not shown). Moreover, the hot tap water sample from building H-4 was contaminated much more than other samples by colour substances, probably iron and manganese. Therefore, the presence of any tested microorganisms’ sequence could not be established in this study for the building H-4. The problem of PCR/qPCR inhibition by DNA impurities is frequently encountered in the case of environmental samples [34,35,36].
According to Inkinen et al., operational conditions may cause to leaching of the pipes, contributing to the changes in tap water microbiome. (Notice that the authors imply that the construction material of the pipes does not greatly affect the forming biomass .) Therefore, the poor DNA quality from building H-4 is probably caused by leaching of metals from pipes installed in the building.
The lack of fluorescence signal from any of the NC samples ensures no contamination in any assay performed in this study.
The study results confirm the contamination of the majority of tested hot tap water samples with Legionella cells. In all tested samples (except of H-4), the levels of L. spp. genome copy number were similar, suggesting comparable hot tap water contamination in all tested buildings. The genomes of L. spp. in 1 mL of hot tap water cover a range of 4.52–15.59. The results of L. pneumophila detection and enumeration indicate the presence of the species in all the tested buildings except SKS (H-4 excluded from the analysis). Building SKS is the newest of all sampling points tested (built within the last 5 years), so the hot tap water installations are less exploited in comparison with the remaining tested buildings. Hence, the accumulation of L. pneumophila bacterial cells in the pipelines might be the lowest. The obtained values seem to be high, indicating the presence of several (up to 12) bacterial cells of L. pneumophila in 1 mL of hot water sample.
Another important aspect is the presence of E. coli bacteria in hot tap water. It can contribute to the risk of epidemiological disease. E. coli sequences were detected in all the tested buildings except D-1 (H-4 excluded from the analysis). The levels of E. coli genome copy number are similar, suggesting comparable hot tap water contamination in all of the tested buildings, like in the case of Legionella genus. Building D-1 is one of the oldest buildings among the tested sampling sites, whereas C-13, where the concentration of E. coli cells was the lowest, was built in 2007. Therefore, the criterion of age of the building/internal installations seems not to be appropriate into the interpretation of the results in this case. The quantities of E. coli are evidently lower than those obtained for L. spp. and L. pneumophila. It is not surprising, because hot tap water provides conditions more suitable for Legionella than Escherichia, as the temperature regimes of hot tap water installations encourage Legionella growth , the fact that was not clearly stated in the literature for Escherichia. Bacteria from Legionella genus are known to be thermotolerant, with growth-limiting temperature around 50 °C (but some strains were isolated even from hot water systems up to 66 °C) ; therefore, their survival abilities in such environments are actually possible. The comparison of the obtained bacterial quantities with the reports of similar research performed in other parts of the world reveals good quality of tap water in Wroclaw. Whiley et al.  quantified L. spp. and L. pneumophila in tap water samples from two water distribution systems in Australia by means of the qPCR method. Despite the values reaching 1238 copies/mL for L. spp. and 1981 copies/mL for L. pneumophila in the summer season, the results for other seasons obtained by Whiley et al. were comparable (in terms of order of magnitude) with those presented in this study. Because the results of this study concern samples collected in summer in a single sampling campaign, seasonal variability cannot be discussed. In the study by Whiley et al., no E. coli cells were detected in two Australian tap water systems, irrespective of the distance from a water treatment plant and the season. It is worth mentioning that Whiley et al. tested the presence of E. coli only by means of ColilertTM trays (IDEXX Laboratories), not the qPCR approach, so dead cells of E. coli species might have been present in the tested samples . In another study by Liu et al. , the presence of L. spp. was detected in all 44 tested tap water samples in northern China, while L. pneumophila was detected only in four out of 44 samples. The gene copy number of L. spp. ranged from 10.47 to 10,715.19 gene copies/ml. The results presented in this study cover the bottom range or are lower than these obtained from Chinese tap water samples. Nevertheless, the concentrations of L. pneumophila gene copies/mL were much lower in the research by Liu et al.  than those presented in this study. Chinese tap water was analysed over an entire year (four sampling campaigns in different seasons), increasing the range of detected bacterial cells .
It must be emphasised that the differentiation of live and dead cells is not possible in this study, so there is no evidence that any of detected and quantified bacterial cells was live and posed any threat to the consumers’ health. The proposed methods for live/dead differentiation might include PMA treatment and light exposure steps during DNA extractions . The usefulness of PMA as the way to differentiate live and dead cells is discussed in the study by Toplitsch et al. , pointing to possible difficulties (i.e. the membrane damage is not the only one determinant of cell death, the turbidity of water samples may affect the PMA binding, short amplicons of PCR/qPCR could not be bound with PMA, giving false results) [40, 41]. Nevertheless, the differentiation between live and dead cells may be crucial in terms of evaluating the health risk to tap water consumers. Because bacteria are known to able to acquire DNA sequences determining the virulence factors in the phenomenon of transformation ; however, the presence of pathogenic species, even in the form of dead cells, should not be neglected. They can provide a reservoir of virulence genes for other living cells.
According to Dietersdorfer et al., viable but non-culturable Legionella cells may proliferate in amoebas and affect human health . The report by Dietersdorfer et al. highlights the insufficiency of culture-dependent methods in studies concerning putative pathogens in tap water. Therefore, the combination of culture-dependent and culture-independent approaches may offer a solution. The comparison of culture-dependent methods with qPCR was performed by Toplitsch et al.  confirming the usefulness of qPCR in such studies.
To prevent the presence of Legionella in tap water, disinfection of water distribution systems is recommended. It has been evidenced that the chloraminated drinking water distribution system in the USA provided water of better quality than the Norwegian system with no residual disinfectant . The crucial role of disinfectant in the prevention of Legionella proliferation in hot water systems was also confirmed by a study by Flannery et al. . Although disinfected tap water is not free from disinfection by-products, as confirmed in the study by Pogorzelec and Piekarska , often constituting other human health risk factors, the abandonment of disinfection would lead to more serious consequences. Nevertheless, as proven in this study, disinfection is not sufficient to prevent the presence of pathogenic microorganisms in hot tap water. Constant monitoring of such bacteria by means of the qPCR method is advised.
Hot tap water samples collected from four out of six buildings of the Wroclaw University of Science and Technology campus were found to contain L. spp., L. pneumophila and E. coli bacterial cells. Because hot tap water is a known reservoir of Legionella species, including those responsible for health problems, such as L. pneumophila, the presence of bacterial cells of the genus is not surprising. As the presence of any opportunistic pathogen in tap water should not be neglected, these findings may be a source of anxiety. The confirmation of the viability of detected bacteria is crucial in the estimation of the consumers’ health risk.
It is worth emphasising that competent living cells dwelling in tap water systems may be able to acquire virulent DNA fragments via the transformation process. Therefore, the presence of bacterial cells of the tested species (particularly L. pneumophila and E. coli), even if dead, might be regarded as the putative source of virulent DNA for other, living bacteria, therefore contributing (indirectly) to the human health risk.
Wolf M, Siedlecka A (2018) Variability of bacterial biofilms under environmental stress conditions in water supply networks: a review. Transylv Rev XXVI(31):1–15
Simoes LC, Simoes M, Vieira MJ (2010) Influence of the diversity of bacterial isolates from drinking water on resistance of biofilms to disinfection. Appl Environ Microbiol 76(19):6673–6679
Balcazar JL, Subirats J, Borrego CM (2015) The role of biofilms as environmental reservoirs of antibiotic resistance. Front Microbiol 6(1216):1–10
Wolf M, Traczewska M, Leluk K, Grzebyk T (2018) Comparability biofilm structure on ITO sensor with forms generated on technical materials. Desalin Water Treat 131:169–179
WHO (2017) Guidelines for drinking water quality
(2018) Emerging home and hospital waterborne pathogens. Perspect Public Health 138(5):250–253
Douterelo I, Jackson M, Solomon C, Boxall J (2016) Microbial analysis of in situ biofilm formation in drinking water distribution systems: implications for monitoring and control of drinking water quality. Appl Microbiol Biotechnol 100:3301–3311
Wong S, Pabbaraju K, Burk V et al (2006) Use of sequence-based typing for investigation of a case of nosocomial legionellosis. J Med Microbiol 55:1707–1710
Rudi K, Berg F, Gaustad E et al (2009) Ratios between Alpha-, Beta- and Gamma-proteobacteria in tap water determined by the ProteoQuant assay. Lett Appl Microbiol 50(1):1–6
Grabińska-Łoniewska A, Wardzyńska G, Pajor E et al (2007) Transmission of specific groups of bacteria through water distribution system. PJM 56(2):129–138
El-Chakhtoura J, Prest E, Saikaly P et al (2015) Dynamics of bacterial communities before and after distribution in a full-scale drinking water network. Water Res 74:180–190
Leginowicz M, Siedlecka A, Piekarska K (2018) Biodiversity and antibiotic resistance of bacteria isolated from tap water in Wrocław, Poland. EPE 44(4):85–98
Pereira R, Peplies J, Höfle M (2017) Development of a genus-specific next generation sequencing approach for sensitive and quantitative determination of the Legionella microbiome in freshwater systems. BMC Microbiol 17(1):1–14
Inkinen J, Kaunisto T, Pursiainen T et al (2014) Drinking water quality and formation of biofilms in an office building during its first year of operation, a full scale study. Water Res 49:83–91
Moore M, Pryor M, Fields B et al (2006) Introduction of monochloramine into a municipal water system: impact on colonization of buildings by Legionella spp. Appl Environ Microbiol 72(1):378–383
Toplitsch D, Platzer S, Pfeifer B et al (2018) Legionella detection in environmental samples as an example for successful implementation of qPCR. Water 10(8):1–11
Lee Y (2013) An evaluation of microbial and chemical contamination sources related to the deterioration of tap water quality in the household water supply system. Int J Environ Res Public Health 10(9):4143–4160
WHO (2007) Legionella and the prevention of legionellosis
Spies K, Pleischl S, Lange B et al (2018) Comparison of the Legiolert™/Quanti-Tray® MPN test for the enumeration of Legionella pneumophila from potable water samples with the German regulatory requirements methods ISO 11731-2 and ISO 11731. Int J Hyg Environ Health 221:1047–1053
Párraga-Niño N, Quero S, Ventós-Alfonso A et al (2018) New system for the detection of Legionella pneumophila in water samples. Talanta 189:324–331
Liu H, Li Y, Huan X et al (2003) Use of the dnaJ gene for the detection and identification of all Legionella pneumophila serogroups and description of the primers used to detect 16S rDNA gene sequences of major members of the genus Legionella. Microbiol Immunol 47(11):859–869
Lazcka O, Javier Del Campo J, Xavier Munoz F (2007) Pathogen detection: a perspective of traditional methods and biosensors. Biosens Bioelectron 22:1205–1217
Lemarchand K, Parthuisot N, Catala P et al (2001) Comparative assessment of epifluorescence microscopy, flow cytometry and solid-phase cytometry used in the enumeration of specific bacteria in water. Aquat Microb Ecol 25:301–309
Prescott A, Fricker C (1993) Use of PNA oligonucleotides for the in situ detection of Escherichia coli in water. Mol Cell Probes 13:261–268
Talukdar P, Rahman M, Rahman M et al (2013) Antimicrobial resistance, virulence factors and genetic diversity of Escherichia coli Isolates from household water supply in Dhaka, Bangladesh. PLOS 8(4):1–8
Subba P, Joshi DR, Bhatta DR (2013) Antibiotic resistance pattern and plasmid profiling of thermotolerant Escherichia coli isolates in drinking water. J Nepal Health Res Counc 11(23):44–48
Coleman B, Salvadori M, McGeer A et al (2012) The role of drinking water in the transmission of antimicrobial-resistant E. coli. Epidemiol Infect 140:633–642
Satish K, Kaiser A, Parkash M et al (2004) Self-transmissible antibiotic resistance to Ampicillin, Streptomycin, and Tetracyclin found in Escherichia coli isolates from contaminated drinking water. J Environ Sci Health A 39(3):651–662
Liu Y, Gilchrist A, Zhang J et al (2008) Detection of viable but nonculturable Escherichia coli O157: H7 bacteria in drinking water and river water. Appl Environ Microbiol 74(5):1502–1507
Regulation of the Minister of Health from December 7, 2017 on the quality of water intended for human consumption, Dz. U. 2017, poz. 2294 (in Polish)
Piekarska K, Zaciera M, Czarny A et al (2011) Application of short-term tests in assessment of atmospheric air pollution. EPE 37(2):85–98
Rybak J, Rogula-Kozłowska W, Jureczko I et al (2019) Monitoring of indoor polycyclic aromatic hydrocarbons using spider webs. Chemosphere 2018:758–766
Piekarska K, Trusz A, Szczęśniak S (2018) Bacteria and fungi in two air handling units with air recirculating module. Energy Build 178:154–164
Dalecka B, Mezule L (2018) Study of potential PCR inhibitors in drinking water for Escherichia coli identification. Agron Res 16:1351–1359
Sidstedt M, Jansson L, Nilsson E et al (2015) Humic substances cause fluorescence inhibition in real-time polymerase chain reaction. Anal Biochem 487:30–37
Gibson K, Schwab K, Spencer S et al (2012) Measuring and mitigating inhibition during quantitative real time PCR analysis of viral nucleic acid extracts from large-volume environmental water samples. Water Res 46:4281–4291
Whiley H, Keegan A, Fallowfield H et al (2014) Detection of Legionella, L. pneumophila and Mycobacterium Avium complex (MAC) along potable water distribution pipelines. Int J Environ Res Public Health 11:7393–7405
Liu L, Xing X, Hu Ch et al (2019) One-year survey of opportunistic premise plumbing pathogens and free-living amoebae in the tap-water of one northern city of China. JES 77:20–31 (in Press)
Alvarez G, Gonzales M, Isabal S et al (2013) Method to quantify live and dead cells in multi-species oral biofilm by real-time PCR with propidium monoazide. AMB Express 3(1):1–8
Toplitsch D, Platzer S, Pfeifer B et al (2018) Legionella detection in environmental samples as an example for successful implementation of qPCR. Water 10:1–11
Banach A, Ciesielski S, Bacza T, Pieczykolan M, Ziembińska-Buczyńska A (2018) Microbial community composition and methanogens’ biodiversity during a temperature shift in a methane fermentation chamber. Environ Technol 3:1–12
Gyles C, Boerlin P (2014) Horizontally transferred genetic elements and their role in pathogenesis of bacterial disease. Vet Pathol 51(2):328–340
Dietersdorfer E, Kirschner A, Schrammel B et al (2018) Starved viable but non-culturable (VBNC) Legionella strains can infect and replicate in amoebae and human macrophages. Water Res 141:428–438
Waak M, LaPara T, Halle C et al (2018) Occurrence of Legionella spp in water-main biofilms from two drinking water distribution systems. Environ Sci Technol 52:7630–7639
Flannery B et al (2006) Reducing Legionella colonization of water systems with monochloramine. Emerg Infect Dis 12(4):588–596
Pogorzelec M, Piekarska K (2018) Application of semipermeable membrane devices for long-term monitoring of polycyclic aromatic hydrocarbons at various stages of drinking water treatment. Sci Total Environ 631(632):1431–1439
This work was supported by the Ministry of Science and Higher Education in Poland (0401/0056/18).
Conflict of interest
The authors have declared that there were no conflicts of interest involved in this work.
Springer Nature remains neutral with regard to jurisdictional claims in published maps and institutional affiliations.
About this article
Cite this article
Wolf-Baca, M., Siedlecka, A. Detection of pathogenic bacteria in hot tap water using the qPCR method: preliminary research. SN Appl. Sci. 1, 840 (2019) doi:10.1007/s42452-019-0533-1
- Legionella spp.
- Legionella pneumophila
- Escherichia coli
- Water distribution system