Water distribution network failure analysis under uncertainty
- 21 Downloads
Failure analysis of water distribution network gains prime importance as it plays a crucial role in meeting the increasing demand for water in megacities. Water interruption can occur due to instances of component failure such as in pipes and valves. Water distribution network is a complex system comprising a variety of components and their interrelations. To avoid sub-optimization, a comprehensive framework for failure analysis is needed, in order to include all parts of water distribution network. The primary aim of the study was to propose a framework for failure analysis in which fuzzy set theory was combined with fault tree analysis as a useful model to deal with uncertainties resulting from unavailability of data. The proposed framework was applied to a water distribution network in Tehran to demonstrate its validity. Water supply interruption was considered a top event in the fault tree. As a result, the occurrence probability of top event was 0.29. According to sensitivity results, isolation valve failure was the critical minimal cut set with the value of 0.16, which shows a 55% decrease in top event probability. Thus, it is concluded that in decision-making process, a focus should be maintained on the critical minimal cut set, while suggesting corrective actions.
KeywordsCritical minimal cut set Fuzzy fault tree analysis Water interruption Water supply system
The authors gratefully acknowledge the help of Tehran Province Water and Wastewater Company (TPWWC) for providing valuable information and data to perform the case study. We also are grateful to the editors and anonymous reviewers for their insightful comments and suggestions.
Compliance with ethical standards
Conflict of interest
The authors declare that they have no conflict of interest.
- Boryczko K, Cieslak BT (2014) Analysis of risk failure in water main pipe network and of delivering poor quality water. Environ Prot Eng 40. http://epe.pwr.wroc.pl/2014/4-2014/Boryczko_4-2014
- Dong HY, Yu DU (2005) Estimation of failure probability of oil and gas transmission pipelines by fuzzy fault tree analysis. J Loss Prev Process Ind 18(4):83–88Google Scholar
- European Commission (2008) Identification and description of hazards for water supply systems. TECHNEAU web. https://www.techneau.org/fileadmin/files/Publications/Publications/Deliverables/D4.1.4.pdf. Accessed 10 Aug 2018
- Hsu HM, Chen TC (1994) Aggregation of fuzzy opinion under group decision making. Fuzzy Sets Syst 79(1):279–285Google Scholar
- Miri Lavasani MR, Wang J, Yang Z, Finlay J (2011) Application of fuzzy fault tree analysis on oil and gas offshore pipelines. Int J Mar Sci Eng 1(1):29–42Google Scholar
- Pan N, Wang H (2007) Assessing failure of bridge construction using fuzzy fault tree analysis. In: 4th international conference on fuzzy system and knowledge discovery, vol 1(2), pp 96–100Google Scholar
- Stamatelatos M, Vesely W, Dugan J, Fragola J, Minarick J, Railsback J (2002) Fault tree handbook with aerospace applications. NASA office of Safety and Mission Assurance. NASA Headquarters. Washington, DC, p 20546. https://elibrary.gsfc.nasa.gov/_assets/doclibBidder/tech_docs/25.%20NASA_Fault_Tree_Handbook_with_Aerospace_Applications%20-%20Copy.pdf. Accessed 3 Mar 2018
- Sugeno M (1999) Fuzzy modelling and control, 1st edn. CRC Press, FloridaGoogle Scholar
- TPWW (2018) Tehran Province Water & Wastewater Co. Web. http://www.tpww.ir/en/aboutus. Accessed 15 June 2018